Online Forum for LMAR IPS GEN 2022-1
In order to submit a post you must be logged in, have downloaded specification documents for this tender and the tender must not be closed.
|RFx Number Status & Type||Details||Date|
LMAR IPS GEN 2022-1
Expression of Interest
Issued by: Southern Alpine Resort Management Board
UNSPSC: 26110000 - Batteries and generators and kinetic power transmission
Tue, 01 March 2022 10:00 am
Wed, 23 March 2022 5:00 pm
Buyer Post #3 - Briefing Questions This post is publicly visible
Please see attached Q&As from the breifing session.
Question: Is logger data available?
Answer: Data has been logged in 2-month blocks. Appropriate irradiation and load profiling has already been done and is not required for your submission.
Question: Are the generator ratings Prime or standby?
Question: Is there a possibility that the generators will be underloaded?
Answer: It is our intention to have the most appropriate generator selected at all times by the PLC. We will be using battery charging load to assist as a dump load.
Question: Do you have a preferred generator synchronization controller
Answer: The design was originally based on the Easy-Gen 3200, but any suitable alternative will be considered.
Question: If a replacement Main Switchboard cannot be built before the white season is there an alternative solution.
Answer: It might be necessary to connect the new generators to the existing switchboard and then upgrade the switchboard after the coming winter season. LMAR are open to this possibility.
Posted on 21 Mar 2022 08:42 by Southern Alpine Resort Management Board