Please clarify the following:
The CFA document lists cable types, No’s and colours to be provided by us for Data, LCD 1, LCD 2 & 3, SCU and PDT to Comms Alcove and/or ICT Room.
These positions are clearly designated on drawing E3. I’d assumed these screens and associated control systems are used for a ‘Turn Out’.
However section 29.04 of the ‘Specification’ details a Despatch & Turnout system to be supplied under a separate contract by the Buninyong Brigade.
It details future positions of twelve (12) monitors at 2300 AFL to a PC position in the ICT Room. Sub-Section (1) ‘Work By Electrical Contractor’ then goes on to detail cable types, runs and termination advice for this system. Are we to install the data cabling component of both systems?
Can you advise where this Access/Security Control Panel will be placed?
I can’t find this speaker nor any other speakers or an amplifier they’d need to run from on any plan that I have for this project nor can I find any specification for a PA. System, please advise?